Aqualis Caleo high-temperature air-to-water heat pumps are specially .. As part of its policy of continual product improvement, CIAT reserves the right to make. AQUACIAT CALEO: the refurbishment solution suitable for both large homes and as those offered by CIAT´s Aqualis Caleo product – were limited to 20kw. Consult CIAT’s NAN brochure on MedicalExpo. Aqualis 2’s added benefits The Aqualis 2 heat pump from CIAT is the key AGEO CALEO – NAD.
|Published (Last):||5 April 2018|
|PDF File Size:||20.84 Mb|
|ePub File Size:||4.43 Mb|
|Price:||Free* [*Free Regsitration Required]|
If this is not the case, aqualiss the procedure below: Easy-to-use microprocessor-based MicroConnect remote control unit with many self-regulating functions. With the unit running, check it thoroughly for any abnormal visual signs or noises. Check the water filters for dirt.
Italiano – All connections must be wired in compliance with the codes and regulations that apply to the location where the system is installed e. Bear in mind the weight and dimensions given in this section. Always disconnect the unit before attempting to wire connections.
The control setpoint is displayed in all other cases. Protect your indoor water circuit with a mix of water, antifreeze and corrosion inhibitor and, possibly, a biocide. Italiano 3- Using litmus paper or a capeo meter, check the pH obtained. Heating is maintained until the frost protection setpoint is reached. Controlled by dry contact J15 In hot water production mode heating, pool, frost protection or domestic hot water modes or when compressor turned off: It is therefore strictly prohibited to bypass it; doing so will create a safety hazard to property and people.
Using a corrosion inhibitor will also prevent the formation of sludge caused primarily by corrosion. Auxiliaries are not ciah If the direction of rotation is wrong: Controlled by dry contact J1 D e u t s ch In all three cases, the circulator can be started back up to protect the exchanger from freezing temperatures. Please contact your boiler manufacturer to find out whether the heating source is compatible with Microconnect control.
Compressor The compressor is fastened to the platform by four 8 mm dia.
NAN – CIAT – PDF Catalogs | Technical Documentation
If so, the terminal may be located anywhere without affecting control see paragraph under table on page Each comes equipped as standard with: Dial selection dot 8-position operation mode dial. Make sure the terminals are securely tightened.
aqua,is Check the glycol content if used. Check for any loose electrical connections. The Online Medical Device Exhibition. The diameters of the tubes are not necessarily the same as those of the unit. Prices are indicative only and may vary by country, with changes in raw materials prices or exchange rates. Particularly suited to renovations, the unit is designed to be connected to an optional mixing tank with multiple connections that supplies water to high-temperature radiators.
Quiet variable speed propeller fan driven by an electronically commutated DC brushless motor. Minutes reverse quickly when pressed and held. NF C in France aqyalis are under the responsibility of the installer. Mandatory annual checks Leaks on the refrigeration circuit. It’s a community-based project which helps to repair anything.
Air/water heat pump – AQUACIAT CALEO – CIAT
English To protect your heating system and avoid all risks of it freezing should it be intentionally or accidentally turned off, we strongly advise that you: Electrical connection tightness check Outdoor coil cleaning Control check Differential water pressure switch Status of liquid sight glass and leak detection 44 5.
The terminal also works as a room thermostat and thus plays an active role in controlling the unit. Moreover, a d3 fault water flow rate fault must not prevent the boiler from caldo. English Installation D e u t s ch – Settings stored in memory for two hours following aqualie power cut – Blue backlit digital display – Maximum dimensions: However, special applications e.
Accordingly, the boiler is still authorised to come on even if this fault appears. For your own comfort, avoid locating the equipment too close to sensitive areas such as bedroom windows. D e u t s ch – Open the valves on the water circuits and make sure water is flowing through the heat pump. Connect the kit and filter to the return water line.
Fault management aqhalis on during test mode.